A: (8) - #18 AWG Class K (16 strand), soft drawn, bare copper conductors w/15 mils (0.38 mm) heat and moisture resistant, polyvinyl chloride (PVC) insulation and jacketed w/ 4 mils (0.10 mm) nylon applied directly to the surface of the insulation.
B: Flame resistant non-hygroscopic fillers (as needed).
C: Mylar binder tape.
D: 45 mils (1.14 mm) of heat and moisture resistant, polyvinyl chloride (PVC) jacket. A ripcord shall be placed underneath the jacket.
(UL) E60544 POWER AND CONTROL TRAY CABLE TYPE TC-ER-JP 18 AWG (0,82 mm2) 8/C TFFN CONDS 600V OIL RES
I SUNLIGHT RESISTANCE DIRECT BURIAL JOIST PULL TCERDirect.com PN TCERJP XXXXX "sequential footage print"
Electrical / Optical Characteristics:
Conductors: ASTM B 3, ASTM B 8, ASTM B 174
Insulation: ICEA S-73-532 (NEMA WC 57), UL 66 for Type TFFN wires
Jacket: ICEA S-73-532 (NEMA WC 57), UL 1277
Conductor Color Code: Black, White, Red, Green, Yellow, Blue, Yellow/Black & White/Blue
Jacket Color: Black
UL THWN 600V
UL Type TC-ER-JP 600V
The insulation is acceptable for use in locations at 90 °C dry. The cable is suitable for use in cable trays, aerial or direct burial installations. The cable is JP rated for installation in accordance with Part II of Article 334.
2023 #18/8 Control Cable 1000 ft. Roll
1000' of cable will be sent via two 500' cables.